What is a GFCI?
A ground fault circuit interrupter, called a GFCI or GFI, is an inexpensive electrical device that can either be installed in your electrical system or built into a power cord to protect you from severe electrical shocks. GFCls have played a key role in reducing electrocutions. Greater use of GFCls could further reduce electrocutions and mitigate thousands of electrical bum and shock injuries still occurring in and around the home each year.
Ground fault protection is integrated into GFCI receptacles and GFCI circuit breakers for installation into your electrical system, especially for circuit outlets in particularly vulnerable areas such as where electrical equipment is near water. Portable GFCls are also available to provide on-the-spot ground fault protection even if a GFCI is not installed on the circuit.
The GFCI is designed to protect people from severe or fatal electric shocks but because a GFCI detects ground faults, it can also prevent some electrical fires and reduce the severity of other fires by interrupting the flow of electric current.
What is a Ground Fault?
A ground fault is an unintentional electrical path between a power source and a grounded surface. Ground faults most often occur when equipment is damaged or defective, such that live electrical parts are no longer adequately protected from unintended contact. If your body provides a path to the ground for this current, you could be burned, severely shocked or electrocuted.
How Do They Work?
A GFCI constantly monitors current flowing through a circuit. If the current flowing into the circuit differs by a very small amount (as little as 0.006 amperes) from the returning current, the GFCI interrupts power faster than a blink of an eye to prevent a lethal dose of electricity. GFCls are designed to operate before the electricity can affect your heartbeat. A GFCI works even on two-slot receptacles.
Here's an example: A bare wire inside an appliance touches its metal case. The case is then charged with electricity. If you touch the appliance with one hand while another part of your body is touching a grounded metal object, such as a water faucet, you will get shocked. If the appliance is plugged into an outlet protected by a GFCI, the power will be shut off before a fatal shock can occur.
Where to Install/Use
The circuits that require GFCI protection are designated by the National Electrical Code (NEC). The NEC typically only applies to new construction/major renovations. The coverage of GFCI protection has gradually increased over the years.
NEC GFCI requirements (and effective date):
- Underwater pool lighting (since 1968)
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
Also consider portable GFCI protection:
- Whenever operating electrically-powered garden equipment (mower, hedge trimmer, edger, etc.)
- With electric tools (drills, saws, sanders, etc.) for do-it-yourself work in and around the house
Download GFCI Fact Sheet